Cause & Consequence
- Uncontrolled release of a flammable gas or liquid
Specific Incident Equipment
6" Fuel gas line
Other than the inspection strategy, which leaves up to a 7 year gap between inspections, there is no process in place to prevent/monitor and repair damage to lagging before corrosion occurs. Whilst the strategy is considered to be robust there is a lack of assurance activities surrounding it to prevent a repeat of the incident since there is no particular reference made to CUI (corrosion under insulation) in the performance standard.
Remove the remaining lagging on the 6” fuel gas line and inspect closely for any signs of corrosion
Inspect insulation local to the area for indications of CUI, damage, or deterioration.
Review the current inspection strategy for this and similar pipework within the standard inspection model.
Raise awareness of CUI and the consequences of damaged paintwork in the corrosion awareness programme
Rate this alert
Latest Alerts & Moments
Our searchable catalogue of hundreds of Safety Alerts and Safety Moments are all designed as learning resources that can help improve workplace safety.