Cause & Consequence
- Uncontrolled release of a flammable gas or liquid
Specific Incident Equipment
Non Return Valve/Water wash tank
Gas had migrated back from the compressor casing into the water wash tank via two block valves, two non return valves and pump. One valve was partially open (a 1/3 of a turn off its seat) the other may have been “passing”. The 2 non return valves cannot be guaranteed to be tight shut off and may “pass”.
Replace all NRV's and associated block valves in the compressor wash systems
Conduct a risk assessment to ensure the safe operation / running of both the compressor and compressor wash skid until the NRV’s and block valves are replaced.
Rate this alert
Latest Alerts & Moments
Our searchable catalogue of hundreds of Safety Alerts and Safety Moments are all designed as learning resources that can help improve workplace safety.