Cause & Consequence
- Failure of vessels or pipework
Specific Incident Equipment
Service Water (also referred to as Fire Water) system (particularly gas cooler & De-aerator Tower)
Inspection of cooler pipe bundle identified a number of further pipes where plugs were missing from an end
Deterioration of the cooler pipe bundle is due to corrosion (from sea water).
Investigate possibility of re-instating second train gas cooler
Investigate possibility of providing double isolation for gas coolers.