Cause & Consequence
- Failure of vessels or pipework
Incident Info Source
Nikki Fell - Petrofac Facilities Management
Specific Incident Equipment
The release source was a cracked weld on a flanged spool bolted directly to an annulus connection on the wellhead.
No details available.
Ensure that as-build drawings are correct - when the incident occurred the well drawings were assembled. The well schematic was found to be incorrect for the make up of the gas lift pipe work.Additional support should have been considered - the gas lift pipe work was isolated and a blind flange installed 3 years prior to the incident. The isolation was downstream of the spring hanger. With movement of the tree all the weight of the pipe work was absorbed by the connection from the 7" annulus.Remove redundant pipe work - the gas lift isolation could have been made at the 7" annulus outlet valve and therefore all the redundant pipe work could have been removed avoiding clutter.
Rate this alert
Latest Alerts & Moments
Our searchable catalogue of hundreds of Safety Alerts and Safety Moments are all designed as learning resources that can help improve workplace safety.