Tundish drain loop seal overcome seeing gas release to module.
Level control did not cut the pump out
NRV found to be passing
- NRV to be changed out
- NRV to be subject to bi-annual change-out within SAP
- Process engineers to review alternative arrangements for drainage pipework
Level control inaccuracy identified. Non-return valve (NRV) found to be passing