Cause & Consequence
- Uncontrolled release of a flammable gas or liquid
Specific Incident Equipment
Pressure transmitter on fuel gas line
This failure is suspected to be due to a combination of normal work hardening of the tube end during assembly and then cracking as a result of mechanical damage which has bent the tube immediately behind the nut. The instrument tubing was not supported sufficiently along its length.
Repair the instrument tubing and provide adequate support.
Rate this alert
Latest Alerts & Moments
Our searchable catalogue of hundreds of Safety Alerts and Safety Moments are all designed as learning resources that can help improve workplace safety.